◆ Starting method: manual
Introduction To Manual Starter
◆ The starter is used to manually start the valve. It is used as a booster mechanism supported by springs. Push the button with a minimum force of 150N, and the spring will be released to form a 700N actuation force on the release valve.
Starting method: manual
Maximum force: 150N
Material: brass, stainless steel, fluorine rubber, silicone resin, aluminum
Size: installation length is 67mm
Installation: Before installation, it must be checked and stay inactivated (the piston rod must be placed below the surface of the starter). If the release valve has been activated, refer to the “Maintenance” chapter to reset it. Loosen the two fixing screws and turn the knob so that the pin is in the proper position. Please only loosen the fixing screws! The two fixing screws must be tightened again, and the torque must not be too high!
◆ Open the seal, pull out the pin, and press the button by hand to start the system. The starter must be reset manually after release.
The launcher reset steps are:
Remove the manual starter from the release valve. Tighten slowly with a tool until you hear a low "click", then tighten it 1/2 turn. (If the tightening torque exceeds 10Nm, stop operation)
Put the safety pin back in place and use a new seal (you may need to turn the button).
Since its establishment, KinFire Technology has a wide range of achievements in the fields of petrochemical...
520 Chang'an Road, Wujiang Economic and Technological Development Zone, Suzhou
Monday to Friday: 8:30 a.m. - 5:30 p.m
Copyright KinFire Technology (Suzhou) Co., Ltd. © 2020 By www.300.cn 苏ICP备20025859号-1